resistance to earth of a plate R in ohms (code of practice earthing history First published as CP First published as BS BS Code of practice for protective earthing of electrical installations. 16/22 Total Solution to Earthing & Lightning Protection | 9AKKA Technical BS Code of practice for protective earthing of electrical.
|Published (Last):||26 June 2007|
|PDF File Size:||20.3 Mb|
|ePub File Size:||8.22 Mb|
|Price:||Free* [*Free Regsitration Required]|
The finished joint should be covered with a heavy coat of bitumen. Soil resistivity may be measured in a similar manner to the establishment of the resistance of the earth electrode. After construction and with the passage of time this moisture content will approach equilibrium with that of the soil, and will usually be dryer than when first laid. Ideally confirmation bz7430 the combined resistance of all the electrodes should be obtained, but the earth resistance codee a structure covering a large area might be quite low and an accurate measurement on a completed structure might be difficult or impossible to achieve.
It should be noted that environmental conditions such as temperature have an bd7430 on earth resistivity with a corresponding decrease in resistivity as temperature rises. The minimum ground cover should not be less than mm and ideally the surrounding soil should be damp.
In high resistivity locations or on rocky ground where long term performance is required, it may be considered necessary to utilize a conductive concrete to improve cdoe contact resistance around an earth rod or strip tape where applicable. Take the smart route to manage medical device compliance.
Current should be passed between the two outer electrodes and the resistance R may be found as the ratio of the voltage between the inside electrodes to the current conducted through the outside electrodes. This is one of the best design reference i have seen. Soil temperature has some effect on the upper layers of strata, but is only important under frosty conditions.
Learn more about the cookies we use and how to change your settings. This may be achieved by making the dimensions in one direction large by comparison to the other two. This model is more closely aligned to the basic theory behind the electrostatic behaviour of an earthing system componentin effect stating more clearly the interactive effect of the value of s which for practical purposes has long been set as being not less than twice the depth of the rod.
Please download Chrome or Firefox or view our browser tips.
The connecting strip to the above ground disconnection point should be fully insulated vor avoid electrolytic action. The resistivity found applies to soil depth a, so by repeating the measurement with different values of athe average resistivity to various depths may be found and the results indicates whether any advantage is to be gained by installing deeply driven electrodes in order to reach strata of a lower resistivity.
Wherever significant continuous earth leakage current is expected, it is recommended that a main electrode of the types described in previous section be provided to which the foundation electrodes can be bonded to provide auxiliary electrodes, thus giving assistance to high fault currents.
It is of particular relevance to: Columns 2 and 3 relate to most of the British Isles, but column 5 is more specific to marshy flats around river estuaries.
BS +A Code of practice for protective earthing of electrical installations
Manish Darji Feb 26, A waterlogged location is not essential unless the soil is sand or gravel. It may be considered necessary to apply numerical methods which are more complex than the formulae given below and software is available to carry out the more detailed calculations.
The basic nature and properties prachice soil in a given location cannot be changed without og expense, and careful consideration of the geology should be used to determine the best location for an earthing system.
This is a amendment to a British Standard on how to meet UK electrical installation earthing requirements.
It also defines selection parameters for the bs740 arrangements and makes clear the need for careful consideration of various site conditions such as soil composition and resistivity. Other shapes are not covered here.
Premium Membership Get access to premium electrical guides, technical articles and much more! For conventional sizes, the resistance is approximately inversely proportional to the linear dimensions, not to the surface areai.
This situation is unlikely to arise if the electrode has a resistance sufficiently low to avoid dangerous voltages to earth. Plates, if used, should be installed as small units of not greater than 1.
It is essential to measure the resistance to earth of any metalwork it is intended to use as an electrode, and to monitor its value at regular intervals afterwardsin order to confirm that it continues to provide an adequate connection to earth. Your basket is empty. Find Similar Items This product falls into the following categories. Care should be taken to avoid a site where water flows over it e.
The resistivity so determined applies to an electrode separation distance a, which is related to the depth of investigation. Click to learn more. The products of corrosion occupy a greater volume than the original metal and cracking might occur.
Measurements and Calculations Of Earth Electrode Systems (BS ) | EEP
They may be used to give an indication of the difficulties that one might face in preparing an adequate design at the chosen location. You may find similar items within these categories by selecting from the choices below:. It should be noted that these types of measurement are not always simple and can often result in a wide range of resistance values depending upon a number of factors such as those mentioned in above paragraph.
The majority of the formulae presented in this section relate to low frequency currents and high frequency examples are not included. Table 1 gives examples of resistivity only. Search all products by. Most pracitce approximation formulae are related to homogenous soil, which is rarely the case in practice, where the different layers of strata will affect the distribution of current passing through the electrode.
It is therefore important to recognize this issue if a long horizontal tape or bare cable is being considered for producing a low earth resistance prractice, even though the impedance will ultimately be limited to a final value see Figure 4.
System earthing involves the provision of a connection to the general mass of earth.